Safe Drinking Water Box for the week of Mar 13 – Mar 19, 2023
Drinking Water Facility Profile: Wauseon City- Lower Maumee Watershed
Owner: Local government, established 1974
Location: Wauseon, OH (Fulton County)
SDWA Permit Status: Active OH2600111
Water Source – surface water; Maumee River, Big Ditch, Stucky Ditch, Big Reservoir (50 acres, 350 million gallons) Little Reservoir (15 acre impoundment, 90 million gallons), Wauseon City Well 001 and 002 are inactive
Purchased water: Delta Village, Lyons Village and Napoleon City
System Type: Community water system Population Served: 7425 Metered Service Connections: 3123
Treatment Capacity: 3 million gallons per day
Current production: 1 million gallons per day
Treatment Process: Class 3 Lime/soda softening plant; process includes lime (softening), aluminum sulfate (coagulation), caustic soda (softening), hydrofluorosilic acid (fluoride), tripolyphosphate (sequestering agent), chlorine (disinfection), carbon dioxide (pH adjustment and stabilization), activated carbon (pretreatment), and potassium permanganate (pretreatment)
Distribution: Wauseon City, Fulton County, Village of Lyons
Finished water Storage: 2 elevated towers: 1 million gallons capacity; underground storage at the water plant: 1 million gallons
Usage: US average household consumption: 400 gallons per day, 100 gallons per person
Contact: Keith Torbet tel 419-335-9871 firstname.lastname@example.org
Latest Compliance Inspection: August 17, 2022 Site Inspection
Sanitary Survey complete, June 28, 2021 (District inspection) performed by the State
Recommendations made in Distribution, Finished Water Storage, Pumps, Treatment; Minor deficiencies noted in Management Operation, Operator Compliance
The following information gathered from federal EPA pertains to the quarter ending Sep 30, 2022 (data last refreshed on EPA database Jan 11, 2023)
Significant Violations History
Maximum Contaminant Level Rule – Stage 2 Disinfectants and by-products of disinfection exceed MCL during all three quarters of 2022 surveyed, from Jan 1 – Sept 30, 2022 archived, measured values range from .085 to .089 mg/L; MCL = .08 mg/L
Consumer Confidence Rule – noted Jan 2019; recorded unaddressed as of Sep 30, 2022.
*Note that drinking water information provided on this site is aggregated from the federal EPA database, state resources and local government sources where available.
EPA publishes violation and enforcement data quarterly, based on the inspection reports of the previous quarter. Water systems, states and EPA take up to three months to verify this data is accurate and complete.
Specific questions about your local water supply should be directed to the facility.
The EPA safe drinking water facilities data available to the public presents what is known to the government based upon the most recently available information for more than one million regulated facilities. EPA and states inspect a percentage of facilities each year, but many facilities, particularly smaller ones, may not have received a recent inspection. It is possible that facilities do have violations that have not yet been discovered, thus are shown as compliant in the system.
EPA cannot positively state that facilities without violations shown in ECHO are necessarily fully compliant with environmental laws. Additionally, some violations at smaller facilities do not need to be reported from the states to EPA. If ECHO shows a recent inspection and the facility is shown with no violations identified, users of the ECHO site can be more confident that the facility is in compliance with federal programs.
The compliance status of smaller facilities that have not had recent inspections or review by EPA or the states may be unknown or only available via state data systems.
All rights reserved 2023 - WTOH - This material may not be reproduced in whole or in part and may not be distributed, |
publicly performed, proxy cached or otherwise used, except with express permission.